California Tank Refurbish Including Tank Repairs and Tank Lining
70,000 gal each x 3 tanks
Diameter = 14 feet, Length ~ 70 ft
San Francisco Bay Area, CA
Tank Testing and Inspection Performed:
- Dew Point Tests
- Barcol Hardness Tests
- Adhesion Tests
- Acetone Sensitivity Tests
- Wireless Temperature Monitors
- 8 inch flange was cut and replaced with a new 8” integral FRP flange (one piece construction).
- ASME RTP-1 standards (eg. thickness and overlays) to install the new FRP laminates for the new flange.
Corrosion barrier removed
Typically 100 mils thick corrosion barrier is removed until sound substrate is achieved.
Test for Sound substrate after corrosion barrier removal
Other Tests to verify substrate is ready for FRP lamination:
- chemical tests
Rebuild internal FRP layers
Resin/Catalyst System: Derakane 411 BPO/DMA w/ post-cure heat
New Flanges Installed
Fill nozzle replaced
Environmentals – Dew Point
Ts – Td > 5 deg F
Ts > 60 deg F
Proper environmental conditions must be maintained during FRP lamination
Professional Tank Repairs and Tank Linings Serving the San Francisco Bay Area
You can expect your job to be handled quickly and with care. Our quality products, experienced fabricators, top-notch on-site technicians, and prompt service are qualities that set us apart from the competition. This is reflected in our multi-decade long relationships with the top refineries, chemical companies, utilities, waste water treatment plants and many others in the Bay Area and Northern California.
Call Us Today (510) 232-0065
You must be logged in to post a comment.